Call Us M-F 8 to 5 PST 1(800)472-1142 or 1(530)926-2900 E-mail us firstname.lastname@example.org
Free Shipping! Continental U.S. Only
Battery Bank Sizing Worksheet
How much storage you would like your battery bank to provide? Base this on the number of days your system will have to provide power without solar input. How many cloudy days in a row are typical for your location? Do you have an alternate source of powergrid intertie or generatorduring these days?
It's not good for batteries to be completely drained (ever), nor is it good for them to be consistently undercharged. It is best to size your battery bank so that it gets regularly charged to capacity.
If you are installing a system for a weekend home you may want to consider a larger battery bank, because your system will have all week to charge and store energy. Alternatively, if you are adding an array as a supplement to a generator-based system, your battery bank can be slightly undersized since the generator can be operated if needed for recharging.
When you sized your solar panel array, you were dealing with watts per hour that you need to produce. Now you will be dealing with amps per hour that you need to store. Remember watts = volts X amps. Now grab a calculator and do the math..........
1. Enter your daily amp-hour requirement.
(Divide watt-hours per day by 12, 24, or 48, depending on your system voltage)
AH/ Day ___________
2. Enter the maximum number of consecutive cloudy weather days expected in your area, or the number of days of autonomy you would like your system to support
(We use 3 - 5 days.)___________
3. Multiply the amp-hour requirement by the number of days. This is the amount of amps-hours your system will need to store.
4. Enter the depth of discharge for the battery you have chosen. This provides a safety factor so that you can avoid over-discharging your battery bank.
This number should not exceed 0.8. We use 50% maximum or 0.5 ___________
5. Divide line 3 by line 4.
6. Select the multiplier (at right) that corresponds to the average winter time ambient temperature your battery bank will experience.
7. Multiply line 5 by line 6. This calculation ensures that your battery bank will have enough capacity to overcome cold weather effects. This number represents the total battery capacity you will need.