PV BATTERY CHARGING CIRCUITS are critical because voltage drop can cause a disproportionate loss of charge current. To charge a battery, a generating device must apply a higher voltage than already exists within the battery. That's why most PV modules are made for 16-18V peak power point. A voltage drop greater than 5% will reduce this necessary voltage difference, and can reduce charge current to the battery by a much greater percentage. Our general recommendation here is to size for a 2-3% voltage drop. If you think that the PV array may be expanded in the future, size the wire for future expansion. Your customer will appreciate that when it comes time to add to the array.
WIND GENERATOR CIRCUITS: At most locations, a wind generator produces its full rated current only during occasional windstorms or gusts. If wire sized for low loss is large and very expensive, you may consider sizing for a voltage drop as high as 10% at the rated current. That loss will only occur occasionally, when energy is most abundant. Consult the wind system's instruction manual.
More techniques for cost reduction
ALUMINUM WIRE may be more economical than copper for some main lines. Power companies use it because it is cheaper than copper and lighter in weight, even though a larger size must be used. It is safe when installed to code with AL-rated terminals. You may wish to consider it for long, expensive runs of #2 or larger. The cost difference fluctuates with the metals market. It is stiff and hard to bend, and not rated for submersible pumps.
HIGH VOLTAGE PV MODULES: Consider using higher voltage modules (18+ volts peak power point, like our BP-585 and BP-590) to compensate for excessive voltage drop. In some cases of long distance, the increased module cost may be lower than the cost of larger wire.
SOLAR TRACKING: Use a solar tracker (by Zomeworks) so that a smaller array can be used, particularly in high summer-use situations (tracking gains the most energy in summer when the sun takes the longest arc through the sky). The smaller PV array will require smaller wire.
WATER WELL PUMPS: Consider a slow-pumping, low power system with a storage tank to accumulate water. This reduces both wire and pipe sizes where long lifts or runs are involved. A PV array-direct pumping system may eliminate a long wire run by using a separate PV array located close to the pump. Our SunRise Submersible, Solar Slowpump, Flowlight Booster Pump and Solar Force Piston Pump are highly efficient DC pumps that are available up to 48V. We also make AC versions and converters to allow use of AC transmitted over great distances. These pumps draw less running current, and far less starting current than conventional AC pumps, thus greatly reducing wire size requirements.
At Wholesale Solar, we will be happy to help find the products that are right for you. For pricing and product information give us a call. We'll also answer any questions you might have about your system. 1 (800) 472-1142
- Off Grid
- Micro-Grid AC
- Grid-Tied Battery
|Pre-Wired Power Centers|
|Racking and Mounts|
|RV & Marine Power|
|Solar Panels by the Pallet|
|Solar Panel Trackers|
|Terms & Conditions|
|Credit Card Authorization|
|Solar Tech TV|